A few weeks ago (September
2018) an Uninterruptible Power Supply was dropped off at the
Low Cost Repair Centre. Although I'd suggested that most problems
could be fixed with a new set of batteries these hadn't arrived
with the equipment. I checked over the UPS but didn't see much
wrong. I did notice a discoloured choke inside the box but what
can go wrong with a choke, so left it and returned the equipment.,
suggesting new batteries were probably needed.
It arrived back a few days later,
again sans batteries, so I removed the darkened choke and fitted
a stout copper link in its place. Whilst the main board was detached
I decided to test all the electrolytic capacitors. To do this
meant removing about a dozen small circuit boards. This was no
easy task as all the boards were soldered into position. Hours
later, and much to my surprise I'd given scores and scores of
the electrolytics a clean bill of health. The designers had apparently
done an excellent job.
Despite all my efforts I'd been
unable to find any information about the equipment so I was still
on a learning curve.
After reassembling everything
I returned the thing for the second time and awaited results.
I heard back and there
was still a problem, so I spoke to the site engineer who told
me it was still troublesome. I suggested buying a new one but
then I discovered a massive jump in price from a 1.5KVA to a
3KVA so agreed to see the UPS for a third time, but insisted
on getting the battery pack so I could run some proper tests.
A clue to the problem was that
he'd reported that smoke had come from the UPS case after a short
time of running on batteries.
Above is the main circuit
board which I removed from the chassis. Dotted around the board
perimeter are the daughter boards, some of which carry extremely
complex circuitry. The main board carries two major areas of
I've already removed a blackened
choke and replaced this with copper wire (centre right) and below
you can see where solder connections have degraded from heat.
I've also removed a component adjacent to the bad choke which
I'll come to later.
Here's a better view.
You can see that the missing part is a capacitor. When looking
over the board I hadn't noticed this, instead vaguely thinking
it was a large relay as only the top view was visible and the
Above are the parts removed
Below is another circuit
board which is fitted on a metal cover under the lid. That other,
small board, was screwed to the lid and carries a battery condition
display and some LEDs
Because I'd now got the
battery pack, I could do some proper tests. On the right (above)
are all the UPS connections which are brought out to a simple
choc block. Not having any documentation I was unsure of two
of the connections. I noticed track visible through the board
that appeared to connect the brown/blue wires (bottom right)
to a relay so initially made the wrong assumption that these
wires indicated the state of the equipment ie. closed meant ON
and open meant OFF, however the wires are marked "Control
Switch" so I checked to see if there was a voltage across
them and found 60 volts DC. To prevent a mistake causing any
damage I found a 270 ohm resistor and discovered only a small
current between the connections,so shorted the wires with a 15
ohm resistor and found it was an on/off switch.
Below is the battery pack.
It uses eight 12 volt 7Ah batteries connected in series. I noted
the fastons don't fit the battery terminals so the battery pack
is not the original one fitted by the manufacturer. That can
at the back is from another project dating from 1917...
Powering the unit from 240 volt
mains produced a start-up routine which apparently is a battery
test. Most types of UPS do this and the nature of the test will
reveal any problem with the battery pack. After a short period
an alarm sounded and clearly, figuring out the display which
now showed a red LED, the batteries had been determined to be
not up to scratch. I've found in the past, with other UPS equipments,
that a battery can be obviously bad, looking bloated or split,
or looking quite normal, but presumably not reaching the correct
level of voltage with a specified current. Whatever the test,
bad batteries seem to be reliably diagnosable but are those above
really bad? The report of smoke made me think a fault was present
that somehow resulted in a false bad battery warning..
Although a simple test isn't
going to prove this one way or another it may give me a clue.
I measured the voltage of each battery with the UPS off, then
on. Each battery looked pretty well nominal with none showing
more than a fraction of a volt lower or higher than average so
I wondered how the UPS would operate if the mains was turned
off. I connected a 60 watt lamp to the mains output and poked
my 15 ohm resistor into the choc block. Much to my suprise the
lamp immediately came on.
I tried a few times and each
time I got 220 volts AC from the unit so I decided to leave it
on and see what happened. At this point I'll mention the purpose
of this UPS. It's to provide a mains voltage for a short period,
if the local mains fails, in order to allow lift passengers to
get out of a lift which would otherwise be stuck. Hence the large
3KVA output, which is necessary to provide a lot of power for
a short period to get the lift to a floor and safety.
Being winter, I wasn't in the
workshop but in our conservatory which was much warmer. By 20
minutes I'd noticed that a slight hot smell had grown to a definite
burning smell and my XYL called out that I should find out where
it was coming from. I already knew the answer so I turned off
the UPS, lifted the lid and gingerly felt around for something
hot. There are a couple of large heatsinks and to my suprise,
both were cold.... but I could feel heat emanating from something.
It was one of the two large chokes (I'd already replaced a blackened
one thinking it might be shorting internally). In fact, it was
incredibly hot so time to do some calculations.
First, a 60 watt light bulb
consumes 270mA of current from 220 volt mains. I hadn't yet noticed
how the choke was connected, but clearly 270mA through a pair
of 1mm wires in parallel shouldn't worry it. I'd already measured
its resistance (not easy) and found it was roughly 35milliohms.
Losses at 270mA should be around 2milliwatts so the choke surely
couldn't be in a mains feed delivering 60 watts. So what about
the battery connections? Well, the batteries are connected in
series to provide around 96 volts so equating the loss at 220
volts to 96 volts gives me 618mA. The loss increases by a whopping
factor of 6.5 to 13milliwatts. No way can the choke get to be
that hot from 13mWatts.
A UPS takes in mains, rectifies
it to something like 320 volts DC and chops it at a figure usually
between 20 and 30KHz then transforms this to generate a lower
AC voltage. This is rectified to produce a supply voltage for
an inverter and a voltage for charging the batteries which are
kept trickle charged until required.
When mains fails, the UPS uses
its batteries to produce a mains supply. Various relays perform
the switchover from the public mains supply to that generated
by the UPS. With luck, and good design of course, any mains powered
equipment will see a loss of mains power for only a very short
time as the changeover relays are energised.
Why on earth would a choke running
such a low current get so hot then? Clearly the UPS is working,
it's not as if it wasn't, and the output surely wouldn't heat
up a choke as much as that observed. It took 20 minutes for the
choke to cool sufficiently to be able to comfortably touch it
and therein lies a clue.
Below, overheated solder connections
to the choke.
Because the UPS can handle 3KVA
it's possible that somewhere in the unit there's a fault which
is drawing a huge current, but not enough to cause the equipment
to stop functioning. The contradiction to this is the absence
of heat anywhere else in the equipment. Let's say the choke is
drawing enough current to make it get very hot... let's say the
dissipation is 40 watts. The current necessary to produce 40
watts in 35mohm is about 34 amps. 20 watts would be produced
by 24 amps, but surely those sort of currents would raise the
temperature of a heatsink, yet both are stone cold.
The answer of course is nothing
to do with DC current (see the capacitor's rating below). The
two chokes are connected in series and intially one was burnt,
then removing this caused to second one to burn. A DC current
through two chokes in series would produce about the same heating
effect in both, but it was only one that appeared to suffer.
Adjacent to the chokes is a capacitor (see below) which from
the size and shape I'd assumed was a relay. I checked it in-circuit
with my ESR meter and found it measured 1.44uF and zero ohms
ESR, but removing it revealed previously hidden markings which
showed it should have been 10uF.
Above, the fried
choke and the pristine-looking duff 1.44uF capacitor.
The two chokes and the capacitor
represent a filter. At this point I hadn't traced exactly where
these fit into the UPS circuitry but what's happening is a ripple
is present which is being inadequately filtered by the duff capacitor.
The ripple component of the current passing through the first
choke is heating, not the copper coil, but the ferrite core of
the choke. The core is getting hotter and hotter to the extent
the copper coil is reaching a temperature sufficient to burn
the enamel insulation. The second coil might also be suffering
the same fate, but by the time the current leaves the first choke
the ripple has been absorbed by the core and isn't bad enough
to cause excessive heating. Removing the first choke and replacing
this with a jumper wire allowed the ripple to reach the second
choke and this was the one I'd found to be incredibly hot. Below..
removing the black component showed it not to be a relay but
Above, from the position
of blue and brown wires which are mains in and mains out, the
filter may be in the internally generated mains output and it's
function would to eliminate roughness in the 50Hz output so a
decent sine-wave results? I traced the circuit and sure enough
the filter is in the mains output.
My guess is the missing 8uF
or so of capacitance is in some way associated with a measured
reduction of the battery charging voltage which is confusing
the battery test routine. Once the capacitor has been replaced,
hopefully the batteries will pass their test.
Going back to some theory (for
the purists: leaving out "j"). What's the impedance
of a perfect new 10uF capacitor at 50Hz ? Answer 318 ohms.
Current drawn at the point where
the mains voltage reaches 220 volts RMS will be 0.7A RMS but
as the mains goes periodically from +220 volts to -220 volts
the current will vary in sympathy from +0.7A to -0.7A. In practice
the output from the UPS will not be a perfect symetrical sinewave
so there may be a residual current. However, the purpose of the
capacitor is to help filter noise and this noise will be related
to the method used by the equipment to generate the mains output.
I imagine to get the best efficiency from the equipment the transistors
fitted to the giant heatsink will be turned on and off very rapidly
and this means that harmonics (mainly odd) of the 50Hz output
voltage will be present. The 10uF capacitor will present a lower
impedance to these harmonics than for 50Hz, for example at 150Hz,
106 ohms, 1KHz, 16 ohms, 10KHz 1.6 ohms. Presumably the UPS designers
calculated the effect of the 10uF capacitor, together with the
pair of chokes to eliminate as much noise as possible from the
output and make this look like a nice clean sinewave within commercial
As a capacitor degrades not
only does its capacitance reduce but its internal resistance
rises also. A degraded capacitor in many stressful applications
will rapidly expire and usually turns into a resistor, goes open
circuit or sometimes just explodes. The example below didn't
get that far but I've seen the remains of many that have ostensibly
vanished leaving shredded aluminium and packing material plastered
around the inside of the equipment.
I'm afraid that capacitor reliability
is going to suffer more and more due to pressures to reduce their
physical size. Bearing in mind that internally generated heat
and ambient temperature are the key factors determining the life
of a capacitor, the smaller the package the less the reliability.
Maybe this explains the size of the replacement I used for this
repair? It's 50% larger, maybe because the suppliers only deal
in components that don't result in customer's complaints? Nowhere
could I find a replacement that matched the (smaller) size of
the one I removed.
After reassembling the UPS I
didn't test it. Instead I waited until my customer arrived to
collect it. I turned it on and after a short time switched on
the battery pack. The battery test routine ran and declared 50%
capacity (which is about right as I'd run the batteries for at
least 20 minutes a few days back), then it gave green lights
(no red alarm LED and no annoying bleep). Success... so I unplugged
the mains supply and the 60 watt lamp immediately lit up. After
a minute all was OK so I turned off the equipment and loaded
it on the wheelbarrow.
I understand there a a few more
of these equipments on site. I wonder how long these will last?
leaving the subject of UPS equipments, I'll mention mine. It's
a small thing rated at 1.5KVA using two 7Ah lead acid batteries
and used to power my computer, display and a small desk lamp.
I've had it for several years and its saved me a lot of bother
as here in the New Forest mains power isn't very reliable. A
few months ago our mains power dropped out and the UPS took up
the job of looking after my computer. After a few minutes the
power returned and all was well, but after a short time we again
lost power. After a few seconds it reappeared and again after
a few minutes the same thing happened again. After something
like ten minutes I was aware of a strange smell not unlike a
steam train. This gradually worsened and I wandered around the
house looking for its source. I traced it to my UPS. A clue was
my computer had turned off. I lifted out the UPS and detached
its case. Inside the two batteries were red hot and the sides
were split with H2S fizzing out of the splits.
Later I checked the circuit board and
found three of the power FETs had gone short-circuit placing
raw AC across the batteries which of course had quickly failed.
I fitted three new FETs and two new batteries and much to my
surprise the UPS was now working normally. I'd already rung the
people responsible for providing our mains supply and put it
to them that the mains voltage must have risen and blown up my
UPS. It took three phone calls before I was promised a cheque
for £40 to cover the cost of new parts.